- Docket Number
- 300 MW
- San Diego County
- Simple Cycle
- Project Status
- Operational (Natural Gas-Fired)
- Project Type
- Application for Certification
The Pio Pico Energy Center (PPEC) is located at 7363 Calzada de la Fuente, San Diego, CA 92154, and is situated on a 10-acre parcel next to the Otay Mesa Energy Center.
PPEC is a 300-megawatt (MW) natural gas-fired, simple-cycle power generation project consisting of three General Electric LMS100 natural gas-fired combustion turbine generators (CTG). Each CTG capable of generating 100 megawatts.
Otay Water District provides potable water directly to the project site through Otay Water District water lines immediately adjacent to the site. The project connects to the Otay Mesa area recycled water main. PPEC’s process water needs are supplied using recycled water and permanent potable water needs consist of drinking water, showers, sinks, toilets, eye wash stations, safety showers, and primary fire protection water. The water balance is based on recycled water quality parameters, which presents a worst-case scenario, based on volume.
The plant uses a partial dry-cooling system (PDCS) in a closed-loop configuration. This allows the plant water consumption to be dramatically decreased in two ways. First, the dry-cooling section reduces the total amount of water evaporated during the cooling process. Second, the closed-loop cooling allows the contaminants in the evaporative water to be concentrated to a much greater extent than in a traditional open-loop cooling system because that water does not pass through the combustion turbine equipment.
Compared to a typical open-loop system with no dry cooling, the PDCS described above decreases the annual plant water consumption by approximately 53 percent and the wastewater production rate by 59 percent.
Notice of Determination for Approval to Increase Tank Capacities for Storage of Raw Water and Wastewater, TN 206923, 12/10/2015, Staff approval Increase tank capacities for storage of raw water and wastewater, increase the height and decrease the footprint of the Water Treatment Building (WTB), and replace the approved reaction tank with two smaller clarifiers.
Order Approving a Petition to Amend to Increase Hourly Heat Input to the Gas Turbines, TN 210349, 02/17/2016, Order No. 16-0210-04, Commission approval of a nominal (approximately 10 percent) increase in hourly heat input.
Approval of Installation of Flagpole, Not in Docket, 07/12/2018, Staff approval to excavate and construct a ground-set flagpole foundation with poured in place concrete per manufacturers recommendation, and/or engineering specifications, complete assembly, rigging, and installation of flagpole with all finish work.
Order Approving Transfer of Operational Control, TN 224900, 10/05/2018, Order No. 18-1003-01b, Commission approval of operational control transfer from NAES Corporation to Southwest Generation Operating Company, LLC.
Attention: Non-hypertext items above will need to be requested from the Compliance Project Manager, along with the document TN number, if provided above.
Power Plant Certification and Exemption Processes
The CEC has the exclusive authority to certify all thermal power plants 50 megawatts (MW) and larger and related facilities proposed for construction in California. The Application for Certification (AFC) process is a certified regulatory program under the California Environmental Quality Act (CEQA). As a certified regulatory program, the CEC does not prepare environmental impact reports (EIRs) in an AFC proceeding, but instead prepares environmental assessment documents that are functionally equivalent to EIRs. A certificate issued by the CEC is in lieu of any permit, certificate, or similar document otherwise required by any state, local or regional agency, or federal agency to the extent permitted by federal law, and supersedes any applicable statute, ordinance, or regulation of any state, local, or regional agency, or federal agency to the extent permitted by federal law.